In this paper, the performance of a three-bed (equal bed) adsorption chiller with mass recovery has been numerically studied. The mass recovery scheme is used to improve the cooling effect and a CFC-free-based sorption chiller driven by the low-grade waste heat or any renewable energy source can be developed for the next generation of refrigeration. Silica gel/water is taken as adsorbent/adsorbate pair for the present chiller. The three-bed adsorption chiller comprises with three adsorber/desorber heat exchanger, one evaporator and one condenser. In the present numerical solution, the heat source temperature variation is taken from 500C to 650C along with coolant inlet temperature at 300C and the chilled water inlet temperature at 140C. In the new strategy, mass recovery process occurs in all beds. The configuration of beds in the three bed chiller with mass recovery were taken as uniform in size. The cycle simulation calculation indicates that the COP value of the three-bed adsorption chiller with mass recovery is 0.6214 with a driven heat source temperature at 65°C in combination with coolant inlet and chilled water inlet temperatures at 30°C and 14°C, respectively.
Renewable Energy Sources, Silica Gel-Water, Mass Recovery, Adsorption Chiller, Cooling Capacity and Coefficient of Performance
- Saha, B.B., Akisawa, A. and Kashiwagi, T. (2001).Solar/Waste heat driven two-stage adsorption chiller: The Prototype Renewable Energy, Vol.23,No.4. p.93-101.
- Khan, M.Z.I., Saha, B.B., Alam, K.C.A., Akisawa, A. and Kashiwagi, T. (2005).Performance investigation on mass recovery three-bed adsorption cycle. International Conference on Mechanical Engineering, p.28-30.
- Khan, M.Z.I., Sultana, S., Akisawa, A. and Kashiwagi, T. (2006).Numerical simulation of advanced adsorption refrigeration chiller with mass recovery. Journal of Naval Architecture and Marine Engineering,Vol.3,No.2. p.59-67.
- Saha, B.B., Koyama, S., Kashiwagi, T. and Akisawa, A. (2003).Waste heat driven dual-mode, multi-stage, multi-bed regenerative adsorption system. International Journal of Refrigeration,Vol.26,p.749-757.
- Saha, B.B., Koyama, S., Lee, J.B., Kuwahara, K., Alam, K.C.A., Hamamoto, Y. Akisawa, A. and Kashiwagi, T. (2003). Performance Evaluation of a low-temperature waste heat driven multi-bed adsorption chiller. International Journal of Multiphase Flow,Vol.29,p.1249-1263.
- Shelton, S.V., Wepfer, J.W. and Miles, D.J.(1990).Ramp wave analysis of the solid/vapor heat pump. ASME Journal Energy Resources Technology,Vol.112,p.69-78.
- Wang, R.Z.(2001). Performance improvement of adsorption cooling by heat and mass recovery operation. International Journal of Refrigeration,Vol.24,p.602-611.
- Alam, K.C.A., Akahira, A. Hamamoto, Y., Akisawa, A. and Kashiwagi, T.(2004). A four-bed mass recovery adsorption refrigeration cycle driven by low temperature waste/renewable heat source. Renewable Energy,Vol.29,p.1461-1475.
- Saha, B.B., Koyama, S., Ng, K.C., Hamamoto, Y. Akisawa, A. and Kashiwagi, T.(2006). Study on a dual-mode, multi-stage, multi-bed regenerative adsorption chiller. Renewable Energy,Vol.31, No.13. p.2076-2090.
- Khan, M.Z.I., Saha, B.B. and Akisawa, A.(2011). Experimental study on a three-bed adsorption chiller. International Journal of Air-Conditioning and Refrigeration,Vol.19, No.4. p.285-290.
International Journal of Sciences is Open Access Journal.
This article is licensed under a Creative Commons Attribution 4.0 International (CC BY 4.0) License.
Author(s) retain the copyrights of this article, though, publication rights are with Alkhaer Publications.